Payment & Shipping Terms:
|Usage:||Insulation Resistance Test And Analyzing||Special For:||Water-cooled Type Power Generator Testing|
|Ouput Voltage:||2500V And 5000V||Range:||0.1MΩ ~ 250GΩ|
|Short Circuit Current:||No Less Than 25mA At 2500V, Max. Output Upto 40mA||Other Functions:||Automatically Calculates The Absorption Ratio And The Polarization Index, Strong Anti-interference Ability, Automatic Discharge After Test, Automatic Save Test Data|
leakage current tester,
high voltage insulation tester
Insulation Resistance Tester , Water-cooled Type Power Generator Insulation Tester, Short-circuit Current 40mA
I.Product Introduction :
Model FKKD2678C Insulation Resistance Tester is specially used for the insulation resistance to Water-cooled power generator, but also can be used for laboratory or field testing insulation testing to other electrical equipment. Output current greater than 25mA. The maximum output voltage of 5000V. Includes high-precision micro-current measurement system, digital boost system. Just use a high-voltage lines and a signal line connecting the test product can be measured. Automatic measurement, the results from the large screen liquid crystal display, and store the results.
II. Main features :
1. 32-bit micro-controller, English user interface, easy to operate.
2. Automatically calculates the absorption ratio and the polarization index, and automatically save 15 seconds, 1 minute, 2 minutes, 10 minutes to facilitate analysis of data per minute.
3. Output current, (2500V, the output is greater than 25mA), short-circuit currents greater than 40mA.
4. A fully enclosed high-voltage generator module technology, the protection of the internal resistance, safe and reliable.Anti-interference ability, to meet the EHV substation on-site operation.
5. Automatic discharge test is completed, and real-time monitoring the discharge process.
III. Main Technical Data
IV. Connection Indication
1. Line Terminal --L terminal or HV output testing terminal
L--"Line" for the high-voltage output, known as the line side, measured by the high voltage cable lead to the end line or tested object , for example, connected to the motor windings.
2. Department of water terminal --G terminal
G----connected with Received water on the sink generator.
3. Terminal base--E terminal
E-earthing terminal,Connected to the generator frame with earthing.
|1||Host machine of the tester FKKD2678C||1pcs|
|2||HV output testing probe between L terminal and tested object||1pcs|
|3||Shielding cable between G terminal and receiving water||1pcs|
|5||Power supply with rechargeable part||1pcs|
|7||Factory testing report||1pcs|
Contact Person: Sales Manager